Factory Sales 750kVA Cummins Silent Gen Power Generator for Sale with Best Price List in China
|FOB Price:||US $1 / set|
|Min. Order:||1 set|
|Min. Order||FOB Price|
|1 set||US $1/ set|
|Production Capacity:||200 Sets|
|Transport Package:||Polyfile Package|
|Payment Terms:||L/C, T/T|
- Model NO.: OCL750
- Installation Method: Portable
- Cooling Method: Water Cooling
- Conditions of Use: Land Use
- Landuse Type of Unit: Automation Type
- Trademark: Oripo
- Origin: China
- Type: Self-Starting Diesel Generator
- Stroke: Four Stroke
- Output Type: AC Three Phase
- Usage: Standby Unit
- Excitation Mode: AC Rotating Exciter
- Specification: 750kva
- HS Code: 8502131000
Engine of generator power plants:soundproof generator
Origin: Manufactured by Dongfeng Cummins Engine Co., Ltd
Start Model: DC24V electric start
Steady Speed Droop:≤1%
6 cylinders ,in-line,4 stroke
ac generator head:
Rated Voltage: 230/400V
Frequency regulation: ≤±0.5 %(stable)
Voltage regulator: standard AVR
brushless,self-excited,AC synchronous, single bearing
auto start control system:
Brand:Smartgen 6110 or Smartgen 6120(with ATS) optional. Customers can also select other brand such as HGM6310, HGM6320, DSE3110, DSE5110, DSE7110 and DSE7210 etc.
(1)Widely used in all types of generator automatic control system for compact structure,advanced circuits,simple connections and high reliability.
(2)LCD display,automatic control, Chinese and English display interface. Can be adjust from front panel, or use the PC through programming interface, also can use a PC via RSR485 interface and monitoring.
(3) Function:high water temperature, low oil pressure, low speed and over load protection,etc.
ATS(Automatic Transfer switch)
It's widely used in hospital,airport,hotel,school and other emergency power supply equipments.
Once the main power failure, the control panel will received the signal to start the genset within 5 seconds, ATS will switch to the load wires to connect genset power supply,and the whole process takes less than 15 seconds. After the main power recovered 30 seconds, ATS automatically switch the load wires to connect main power supply,the genset will stop after running 180 seconds
Rubber paad mounting isolate base from engine/generator assembly Rubber pad mountings isolate base from engine/generator assembly make it stable:
Intermal high-efficent prevent silencer. which can reduce the niise in outlet smoking vent
Super Soundproof/Silent Box:
1. Excellent ventilation
2. Oil tank mounted on base frame for 12 Hours working
3. Highly Corrosion Resistant construction
4. Excellent Access for Maintenance
5. Security and Safety
6. 1m<80DBA / 7m<70DBA
|GENSET TYPE||open/sound proof/weather proof/trailer/container|
|Genset output power range||23kva-2000kva|
|Cooling system||Water cooled|
|Starting system||24V DC electric starting|
|output type||AC three phase/single phase|
|Motor||Brushless & self-excited|
|R.R.I.Suppression||BS EN 61000-6-4/BS EN61000-6-2|
Optional accessories /spare parts:
Sound and water proof enclosure
Trailer/ Movable power station
Battery charger by main supply
Jacket water heater
Diesel oil heater
Automatic transfer switches (ATS) & paralleling system
Extra fuel tank
1. When to replace the lubricant oil?
It depends on different type generator, different brand engines and different power.
For detail maintenance steps, please refer to the maintenance schedule in ORIPO diesel generator set manual.
Here are some methods to check the lubricant oil:
a.Using two glass tubes(0.5cm diameter, 20cm long ), each filled with 19cm of new oil and used oil, seal the two tubes while upside down, take the record of the bubbles rising time, if the difference is more than 20%, then the used oil should be replaced.b.Drop the new oil and used oil on a white filter paper,compare them, if the used oil droplet has more black spots, indicating that the oil is not bad, should be replaced; if it became dark brown oil, then is bad, should be replaced.
2.What causes the too high water temperature of the diesel generator?
c.the fan belt, water pump belt is too loose;
D.the water tank is too dirty (internal or external).